Stationary dry aerosols fire extinguishing components are designed for use as part of a fire extinguishing system. The fire extinguishing system shall activate these fire extinguishing components.
The fire extinguishing component consists of a container filled with a dry solid extinguishing agent, which after activation is discharged as a dry aerosol to extinguish the fire.
The fire extinguishing component shall be suitable to extinguishing following EN 2 fire classes:
- Extinguishing of class A fires (solids)
- Extinguishing of class B fires (liquids or liquefying substances)
- Extinguishing of class C fires (gases)
- Extinguishing of class F fires (boiling oils and fat fires)
Applicable standards in this BRL-K23001/05 are:
- CEN/TR 15276-1 Fixed fire fighting systems - Condensedaerosol extinguishing systems - Part 1: Requirements and test methods for components
- ISO 15779 Condensed aerosol fire extinguishing systems - Requirements and test methods for components and system design, installation and maintenance - General requirements
Melting plastics are defined as class A fires.
Fires caused by electrical short circuits will lead to class A, B and C fires.
Fire detection companies, system administrators.
'BRL K23001-05 Product Certification Scheme for nonpressurized condensed aerosol generators and components used in fixed fire extinguishing systems' outlines performance criteria for system components and requirements for test methods.
In addition, the BRL outlines requirements for the company’s quality management system. This includes requirements for internal quality control processes, procedures, work instructions and personnel.
Certification of your company based on ‘BRL K23001-05’ starts with an application, after which you receive a fee proposal. You can enter into a certification agreement with Kiwa on the basis of this fee proposal. Kiwa assesses whether the criteria for certification are met based on an independent acceptance audit. Certification will follow upon a positive audit outcome. However, if non-compliances are identified, you shall rectify these first.
Annual inspections are conducted to establish that the certified processes and completes works continue to comply with the applicable requirements in order to maintain your certification based on ‘BRL K23001-05 Product Certification Scheme for nonpressurized condensed aerosol generators and components used in fixed fire extinguishing systems’ after initial certification.
For certified companies, click here.
Why Kiwa NCP?
Kiwa NCP is a leading certification body for the certification (accreditation) of fire protection and security companies, also called Fire Safety & Security (FSS).
Kiwa NCP is an independent Certification Body that determines whether a company meets the quality requirements. A Kiwa NCP Certificate provides the occupant with a well-founded confidence in the quality of the certified company and its services, such as testing, commissioning and maintaining systems.